WARNING: Before proceeding, be sure the area is well ventilated. Turn the thermostat OFF. If the blower is running, wait until it stops automatically. Turn OFF the gas and electrical power supplies to the furnace. Check all metal parts and surfaces to be
EXTERNAL AIR FILTERS
Every time the external air filters are changed the following items should be visually inspected:
If during the inspection of your furnace, you find any of the following conditions:
How to Clean your Filter
NOTE: The spring-loaded safety cut-off switch, mounted at the blower deck will automatically cut off the electrical power supply to the furnace when the furnace blower access panel/door is removed. As a safety precaution, all electrical power and the gas
WARNING: Make sure you DO NOT move the clip on weight on the indoor fan wheel when cleaning the wheel. This weight is used to balance the wheel. Moving the weight will cause the fan wheel to vibrate.
SERVICE INFORMATION TROUBLESHOOTING PROBLEMS
If your furnace is not operating correctly, the following visual checks should be made before contacting your local contractor, dealer, or service provider.
FURNACE CONTROL DIAGNOSTICS
SLOW GREEN FLASH
DOUBLE AMBER FLASH
SLOW AMBER FLASH
RAPID RED FLASHES
FURNACE MAINTENANCE - DEALER/CONTRACTOR
The furnace should be cleaned and adjusted by a certified dealer or qualified service contractor once a year or before the start of every heating season. The following items must be cleaned and serviced or replaced if there are signs of deterioration.
REPLACEMENT PARTS LIST