DATE OF INSPECTION
The area around and the path to the eyewash is not obstructed.
Verify nozzle caps are in place and the nozzles, nozzle caps, and bowl are clean and sanitary.
Push hands-free valve to full open position. Water must flow within 1 second. Run minimum 60 seconds
Verify that nozzle caps come off when the eyewash is activated and water is flowing.
Verify water continues to flow until manually turned off and can be used hand-free by pushing water valve activator..
Look at the water flow pattern. It should provide a non-injurious flow from both nozzle streams.
The water should flow from both streams and rise to an equal height in a pattern that will flush both eyes simultaneously.
Water flow covers area shown in test gauge, maximum 8” above spray heads, minimum 33" above the floor.
Add or drag pictures
Use thermometer to confirm water temperature is tepid, minimum 60°F, maximum 100°F.
Continue to run eyewash and flush until water is clear.
Report problems to the Safety Manager. Sign in the box to confirm inspection results.
Click here to sign
Source: Urethane Sciences, LLC (Community Member)