Direct Drive Supply and Exhaust Fans
Before greasing, be sure fittings are clean and free from dirt. Remove grease relief plug or plate and, using a low-pressure grease gun, pump in the required grease. Do not over-grease. Re-lubrication intervals are specified in Table 12. After re-lubricating, allow motor to run for 10 minutes before replacing relief hardware.
IMPORTANT: In general, it is not recommended to mix greases of different brands. The mixing of different types of thickeners may destroy the composition and physical properties of the grease. In the event that a different grease is required by the end user, the following steps can be taken. Using the Lubricating Instructions, open grease outlet and purge the system as much as possible of the old or unwanted grease. Repeat this same operation after one week of service.
Refrigeration Circuit Components
Condensate Drain Pan and Drain
Energy Conservation Wheel
The wheel is somewhat self-cleaning through its normal action of rotating in and out of counter current airflow streams.
In the event that routine quarterly inspection indicates that there is dirt or dust buildup within the wheel causing an excessive pressure drop, then wheel cleaning should be performed as follows:
Check for gas leaks
MANUAL SAFETY SHUT OFF VALVE
Check for gas leaks.
DIRECT SPARK IGNITER
Check for cracked ceramics, excessive carbon residue, or erosion of the electrode. Replace as required.
Check that gas valve seat is not leaking.
Soft brush or vacuum inside burner, at burner ports, and at air inlet between burner and manifold pipe to eliminate accumulation of lint and/or dirt.
Inspect for cracks, sagging, bending, or distortion. Clean with vacuum and/or stiff brush.
Clean with compressed air or vacuum.
Venting must be intact. Using a flashlight, look for obstructions, cracks on the pipe, gaps in the sealed areas, or corrosion. Clean vent terminal.
Check for blockages.
Electric Heater Wiring and Wiring Connections
Check all wiring connections. Tighten as necessary. Check internal wiring. Replace as necessary with type THHN 221°F (105°C), 600V, 16-gauge wire or equivalent.
Check heater control panel for dust/dirt and moisture. Clean as necessary.
Check heating elements for dust/dirt buildup and/or broken elements. Replace elements and/or clean elements with low pressure air as necessary. Check element male/female chassis insulators for breaks and/or cracks. Replace as necessary. Check element support frame insulators. Replace missing or broken insulators as necessary
Filters should be checked for dirt restriction on a monthly basis (or as required). Replace filters with filters of equal specification when they appear dirty.
Source: Carrier (www.shareddocs.com)