Oil Level Check:
TABLE 4-1 – FAN BEARING – LUBRICATION INTERVALS
CAUTION: Never use the scroll compressor to pump the re frig er ant system down into a vac u um. Doing so will cause in ter nal arcing of the compressor motor, which will result in failure of com pressor.
Fan Bearing Lubrication
Re-lubrication is generally accompanied by a tem po rary rise in operating tem per a ture. Excess grease will be purged at seals.
Lu bri cant must be free of any chemical impurities such as free acid or